Soundproof canopy 100kva generator with AD type fuel pump EFC electronic governor
1.Strict Test program which includes 50% load, 75%load,100% load, 110% load and all protection function (overspeed stop, high water temperature, low oil pressure, battery charging fail, emergency stop)
2.Automatic controller and safety shut-down functions.
3.Battery charger and 24V starting batteries and connecting with cables.
4.Industrial silencer and flexible exhaust hose.
5.8-hours operation base tank.
6. Brushless, Self-excited, IP23, insulation class H alternator
7.Powered by Cummins engine
Data of 100kva generator:
230/400VAC,50Hz,0.8PF (lag),Three phase four wires
Generator set specifications
Steady Voltage Regulation
BS EN 61000-6-4 / BS EN 61000-6-2
Fuel Consumption Rate ,g/kw.h(L/hr)
Starting Battery Capacity ,A/hrhhr
Total Coolant Capacity ,L
In-line 6 Cylinder,4 Cycle
Turbo, Air/ Air Cooling
PB type Fuel Pump
Rated Speed ,rpm
24V ,Negative ground
Battery Charging System
Temperature Rise in Standard
125°C(When Ambient Temp.is 40 °C)
Brushless & Self-excited
No load<1.5% Non-Distorting balanced linear load<5%
Exhaust air flow
Max Back Pressure
Air Intake System
Max Intake Restriction
Total Lubricant Capacity
Engine Oil Tank Capacity
Oil Pressure at Rated Speed
Main Standard parts of ORIPO 100kva generator:
Above photos just for reference.
OPTIONAL ACCESSORIES/SPARE PARTS:
-Sound and water proof enclosure
-Trailer/Movable power station
-Jacket water heater
-Diesel oil heater
-Automatic transfer switches(ATS) & paralleling system
-Extra fuel tank
-Fuel water separator
Packaging & Shipping
According to our customers’ situation or request, we will make suitable generator proposals, Technical data and documents offer.
Warranty will be 1 year or 1000 working hour from the notify date of awiting transportation.During the guarantee period, Oripo would be responsible for problems caused by quality of production or raw material, except the damageable spare parts caused by incorrect man-made operation. After expiration, Oripo provides cost maintenance for generators.
a.1year or 1000working hours whichever comes first!
b.Spare parts will send to you for free during warranty period,if confirm its defect caused by the manufacturer.
c.Pre-sale service & After-sale service avaible, free technical service support.
1.From Guangzhou Baiyun International airport to Oripo:
a.It takes about 1 hour by car/taxi,it is about 58 kilometer;
b.Or take the subway from JiChangNan station to HanXiChangLong Station(you need to transfer at the TiYuXiLu station to PanYu direction), then take a taxi to Oripo, it will take about 1.5 hour.
2.From Canton fair complex to Oripo:
a. It takes about 30 minutes by car / taxi, it is about 32 kilometer;
b. Take the subway from XinGangDong Station / PaZhou station to HanXiChangLong Station, then take a taxi to Oripo, It will take about 1 hour.
What causes the too high water temperature of the diesel generator?
c.the fan belt, water pump belt is too loose;
D.the water tank is too dirty (internal or external).
More question of 100kva generator, welcome to discuss.
Established in 1998, Foshan Oripo Power Engineering Co., Ltd. is one of the leading manufacturers of diesel generator sets worldwide, with over 20000 square meters of factory area and nearly 400 staff members. Our headquarters is located in Foshan City, adjacent to Guangzhou, which is the trade center of Guangdong Province. Our other 17 branches are all over the domestic and overseas markets.
We mainly deal in different famous brands' diesel generator sets, soundproof and rainproof canopies, ... View detail