Industrial Cables-British Standard 6241Y/6242Y/ 6243Y to BS 6004
Application and Description
These cables are suitable for fixed installation in dry or damp premises on walls, boards or trays, in channels or embedded in plaster. They should be laid in conduit or trunking where mechanical protection is required.
- Fine bare copper strands - Stranding to IEC 60228 CL-1 or 2 - PVC insulation type TI1 to BS 7655 - The core or cores shall be laid parallel with the uninsulated circuit protective conductor - For twin cores, the protective conductor centrally placed between cores in same plane - For 3 cores, the protective conductor centrally placed between black and grey cores in same plane - PVC sheath type T6 to BS 7655
2 cores: brown and blue, or, for 2 × 1.0 and 2 × 1.5 cables, brown and brown 3 cores: brown, black (centre core) and grey
- Working voltage: 300/500v - Test voltage: 2000 volts - Minimum bending radius: 4xOverall diameter - Flexing temperature: -15º C to +70º C - Short circuit temperature: +160º C - Flame retardant: IEC 60332.1 - Insulation resistance: 10 MΩxkm